AS/NZS SECTION 9 – HOT. LAYER SMOKE CONTROL SYSTEMS. Hot layer smoke control systems shall comply with this Section and the relevant. The draft version of Australian Standard AS The use of ventilation and air conditioning in building Part 1: Fire and smoke control in. Download Citation on ResearchGate | AS Impact on design – fire and smoke control | The thrust of Part I of Standard AS is to ensure that air.
|Country:||United Arab Emirates|
|Published (Last):||15 January 2008|
|PDF File Size:||16.6 Mb|
|ePub File Size:||4.16 Mb|
|Price:||Free* [*Free Regsitration Required]|
FPA Australia | AS Released for Public Comment
Detection and initiation of smoke controls systems have been transferred to AS Carpark ventilation systems The function of carpark ventilation systems now requires all fans not required to shut down be provided with an electrical supply from a clearly labelled dedicated main switch separate from those used to control the remainder of the electrical installation.
Mandatory requirements for Baseline Data have been included to match the maintenance requirements of AS The revision AS Devices that prevent the spread of flames are required where ductwork within the building exceeds 10m and where exposed flame or embers are present as part of the cooking process, spark arresters are required where the appliance can produce sparks such as wood fired pizza ovens and similar appliances. For further information, please contact us.
It specifies the requirements for exhaust capacities, smoke reservoirs, plenums, smoke curtains, intakes, and make up air. Along with AS Walker Fire Protection provided fire protection services for the project to Channel Nine. This information must be provided to building owners to maintain their HVAC systems with regard to fire and smoke control, and also to assist future designers making alterations to systems within the building.
It includes the design information, aas instruction, smoke control schematics, commissioning data, testing results and fire and smoke damper schedules.
Subscribe to our mailing list. This has created better alignment between these standards in relation to the deemed-to-satisfy requirements. Featuring the historic Gatwick Hotel in St Kilda.
The function of carpark ventilation systems now requires all fans not required to shut down be provided with an electrical supply from a clearly labelled dedicated main switch separate from those used to control the remainder of the electrical installation. The content for this section has been taken from the superseded AS A section relating to Hot Layer smoke control has been added.
For more information Contact Us. The requirements for design and commissioning data to be provided at handover, known as Baseline Data, is now detailed in AS Jet Fans used for carpark ventilation are now required to shut down in fire mode or activation of the sprinkler system under the new standard.
Subscribe to the mailing list to receive Advisory Notes in your inbox. The Australian Standard AS Hot layer smoke control A section relating to Hot Layer smoke control has been added.
Coombs expert to present at Fire Australia The standard now requires wall mounted fire dampers to carry the same insulation rating as the wall unless they are connected to 2 meters of rigid duct. Baseline data The requirements for design and commissioning data to be provided at handover, known as Baseline Data, is now detailed in AS Improved clarity has been added to the way smoke dampers are constructed and installed across the standards.
The way openings in walls and floors are protected against fire has been re-written to include a clause 3. April 23, in News A. Intumescent fire dampers can overcome the insulation requirements for installations where 2 meters of rigid duct is not used.